<?php



## XUPS-MIB
if ($device['os'] == "powerware")
{
  echo("XUPS-MIB ");

  # XUPS-MIB::xupsBatVoltage.0 = INTEGER: 51
  $oids = snmp_walk($device, "xupsBatVoltage", "-Osqn", "XUPS-MIB");
  if ($debug) { echo($oids."\n"); }
  $oids = trim($oids);
  foreach (explode("\n", $oids) as $data)
  {
    $data = trim($data);
    if ($data)
    {
      list($oid,$descr) = explode(" ", $data,2);
      $split_oid = explode('.',$oid);
      $volt_id = $split_oid[count($split_oid)-1];
      $volt_oid  = ".1.3.6.1.4.1.534.1.2.2.$volt_id";
      $divisor = 1;
      $volt = snmp_get($device, $volt_oid, "-O vq") / $divisor;
      $descr = "Battery" . (count(explode("\n",$oids)) == 1 ? '' : ' ' . ($volt_id+1));
      $type = "xups";
      $index = '1.2.5.'.$volt_id;

      discover_sensor($valid['sensor'], 'voltage', $device, $volt_oid, $index, $type, $descr, $divisor, '1', NULL, NULL, NULL, NULL, $volt);
    }
  }

  # XUPS-MIB::xupsInputNumPhases.0 = INTEGER: 1
  $oids = trim(snmp_walk($device, "xupsInputNumPhases", "-OsqnU", "XUPS-MIB"));
  if ($debug) { echo($oids."\n"); }
  list($unused,$numPhase) = explode(' ',$oids);
  for($i = 1; $i <= $numPhase;$i++)
  {
    # XUPS-MIB::xupsInputVoltage.1 = INTEGER: 228
    $volt_oid = ".1.3.6.1.4.1.534.1.3.4.1.2.$i";
    $descr    = "Output"; if ($numPhase > 1) $descr .= " Phase $i";
    $type     = "xups";
    $divisor  = 1;
    $current  = snmp_get($device, $volt_oid, "-Oqv") / $divisor;
    $index    = '3.4.1.2.'.$i;

    discover_sensor($valid['sensor'], 'voltage', $device, $volt_oid, $index, $type, $descr, $divisor, '1', NULL, NULL, NULL, NULL, $current);
  }

  # XUPS-MIB::xupsOutputNumPhases.0 = INTEGER: 1
  $oids = trim(snmp_walk($device, "xupsOutputNumPhases", "-OsqnU"));
  if ($debug) { echo($oids."\n"); }
  list($unused,$numPhase) = explode(' ',$oids);
  for($i = 1; $i <= $numPhase;$i++)
  {
    # XUPS-MIB::xupsOutputVoltage.1 = INTEGER: 228
    $volt_oid = ".1.3.6.1.4.1.534.1.4.4.1.2.$i";
    $descr    = "Output"; if ($numPhase > 1) $descr .= " Phase $i";
    $type     = "xups";
    $divisor  = 1;
    $current  = snmp_get($device, $volt_oid, "-Oqv") / $divisor;
    $index    = '4.4.1.2.'.$i;

    discover_sensor($valid['sensor'], 'voltage', $device, $volt_oid, $index, $type, $descr, $divisor, '1', NULL, NULL, NULL, NULL, $current);
  }

  # XUPS-MIB::xupsBypassNumPhases.0 = INTEGER: 1
  $oids = trim(snmp_walk($device, "xupsBypassNumPhases", "-OsqnU"));
  if ($debug) { echo($oids."\n"); }
  list($unused,$numPhase) = explode(' ',$oids);
  for($i = 1; $i <= $numPhase;$i++)
  {
    $volt_oid = ".1.3.6.1.4.1.534.1.5.3.1.2.$i";
    $descr    = "Bypass"; if ($numPhase > 1) $descr .= " Phase $i";
    $type     = "xups";
    $divisor  = 1;
    $current  = snmp_get($device, $volt_oid, "-Oqv") / $divisor;
    $index    = '5.3.1.2.'.$i;

    discover_sensor($valid['sensor'], 'voltage', $device, $volt_oid, $index, $type, $descr, $divisor, '1', NULL, NULL, NULL, NULL, $current);
  }
}

?>